— All bolts, screws, etc. that come into contact with the liquid being pressed must be made of bronze or corrosion resistant material.
— Supplied with fire pump, automatic air relief valve, housing cooling valve and manometers.
— The bearings must have a L-10 life of at least 5000 hours in the case of maximum loading.
— Fire pumps should be supplied with at least 4 winding soft seals and a watering ring between them. If no watering ring is to be installed, there must be at least 5 winding soft packings.
— The fire pump impeller, wear rings, shaft, irrigation ring and glene must be made of corrosion resistant material.
— STANDARD UL / FM fire pumps are manufactured according to the following material combinations:
Flow rate 750-1000-1250-1500 GPM
Head up to 200 PSI
Body Pressure (pmax) 16 bar (25 bar)
Speed up to 3000 rpm